Lighting Protection | Astro Lumi Canopy
For in-stock items orders received before 2pm (Monday-Friday) are generally dispatched for delivery on the following working day (Monday-Friday).
Astroflame Luminaire Canopies stop the passage of fire and smoke, for up to 60 minutes, through luminaire light fittings in a fire rated ceiling.
Without the fire rated canopy in place, fire and smoke will penetrate the recessed light fitting in seconds and spread into the void or room above endangering lives and property.
The Astro Lumi Canopy provides 60 minutes fire protection by completely containing the fire and smoke within the cover. In normal (non-fire) conditions the heat from the light fitting can dissipate through the canopy fabric.
The fire canopies are easy to fit from either side of the ceiling and need no additional supports. They can also be easily removed and replaced for lighting maintenance.
BS 476 Part 23: 1987, Clause 5 - 60 minutes. Assessed for use with suspended ceiling system - 60 minutes. Assembly protected with fire – rated suspended ceiling system – 30 minutes.
|Product Code||Product Description||Size||Height|
|AFLUMICANS||Astro Luminaire Canopy Small||300x300mm||150mm|
|AFLUMICANM||Astro Luminaire Canopy Medium||600x300mm||150mm|
|AFLUMICANL||Astro Luminaire Canopy Large||600x600mm||150mm|
|AFLUMICANXL||Astro Luminaire Canopy X Large||1200x300mm||150mm|
|AFLUMICANXXL||Astro Luminaire Canopy XX Large||1200x600mm||150mm|
Please contact us and quote the following - Quantity / Product Code / Product Description / size
Typical example:- 10 / AFLUMICANL / Astro Luminaire Canopy Large / 600x600x150mm
Fitting Instructions Recessed Luminaire within a suspended ceiling grid.
Remove hood and fittings from packaging, check contents and unfold canopy.
Place the hood over the luminaire, aligning cable entry with lighting cable.
Thread the cable through the cable entry holes.
Secure the hood to the ceiling grid with steel, self tapping screws (min 4mm diameter & 12mm length) by screwing through the hood and into the bulb of the grid at 80mm centres.
Fold the corner tab tightly over the grid section and secure.
The hood is now installed.
Replace the surrounding tiles & finish the installation of the luminaire as recommended by the manufacturer.
All recessed lighting hoods have single & dual cable access. For dual cable access remove the sealing bolt as shown above.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on tel 01329 844 500 or email email@example.com
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 – Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
For further information on installation requirements please refer to the lighting fitting or suspended ceiling manufacturer data to ensure the compatibility of this product, if in doubt please contact the technical team on: tel 01329 844 500 or email firstname.lastname@example.org
The product does not present any known health hazards during or after installation. Normal good industrial and personal hygiene practices should be observed. For further information on health and safety requirements please contact the technical team on: tel 01329 844 500 or email email@example.com
Download and review the following available data sheets for this product.
For in-stock items orders received before 2pm (Monday-Friday) are generally dispatched for delivery on the following working day (Monday-Friday). All dates quoted for despatch are estimates only and are not guaranteed. We will endeavour to meet these dates but shall have no liability for any delay in despatch or delivery or any damage or loss occasioned thereby. We may deliver products pursuant to any order by instalments. If we are unable to deliver the goods for any reason,you will be contacted and you will not be obliged to pay for the goods which have not been delivered, you also have the option to cancel the goods that have been delivered, however we shall not be liable for any loss of income or profit which may have been caused by the delay or non delivery of goods.
For information about our returns policy please click here.
If you've got a question about this product or need some technical help get in touch with the Astroflame sales or technical team to discuss your requirements today. We are open Monday to Friday 8:00am to 5:30pm. You can always contact us on the following:
Web Page Last Modified: 23rd June 2023
or click "x" to close this box.